Hamworthy Fleet 350v boiler repairs
Our client employed our services to investigate a leak on the heating system. Boiler module no1 had failed and the heating system water was being discharged via the condense pipework. Due to the building housing over 100 employee’s a temporary heating and hot water packaged boiler was installed.
A replacement heat exchanger was installed, and the remaining 5 boiler modules were completely stripped down, and all gaskets were replaced. The heat exchangers were flushed through and the condense pipework was removed and cleaned. The heating system strainers and the air- dirt separator was cleaned, and the heating system water was tested and dosed accordingly. All 6 boilers modules had replacement burners and once reassembled the boilers were recommissioned. The gas installation pipework was tested, and a gas safety certificate was issued upon completion of the works.